If this is your first visit, be sure to
check out the FAQ by clicking the
link above. You may have to register
before you can post: click the register link above to proceed. To start viewing messages,
select the forum that you want to visit from the selection below.
location, or slang is the difference. they are referring to standard house current of single phase 120V and 240V, some times referred to as 110V and 220V. put a meter on your house and you could get any where from 110V to 125V same with the 240V side. power is a little different depending on location. if you have 110V and 220V at your house you are fine.
thanks for the help
hope i helped
feel free to shoot me an e-mail direct i have time to chat. email@example.com summer is here, plant a tree. if you don't have space or time to plant one sponsor some one else to plant one for you. a tree is an investment in our planet, help it out.
Hey TC, curious what you want to be cutting with the 375? I have a 375 and when I bought it I thought I would be slicing through everything! It is great for certain applications but do your research so you don't end up disappointed.
Take into consideration the guage of the material and the cfm output you will need to cut well. There is more to cutting mobil than just being able to plug into a 110V outlet.
I would search all the previous threads regarding the 375 before making a decision.
Maxstar 150 STL
Blue Star 185 DX
I'am considering buying a spectrum 375 with dual input voltage of 115 or 230. What is the difference between 220 and 230 or 115 and 110.
The difference is this. "Modern" power supplied is 120/240V. Anything within 10% of those (108V-132V and 216V-264V) is considered within tolerance.
If you are plugged into a circuit (say a wall outlet) with a voltage reading of 120V with the equipment off and you start to pull a lot of current, the voltage will sag. As the voltage sags, the current will increase proportionally to the sag. In other words, drawing lots of current makes the voltage drop which results in more current draw, the voltage dropping more and further increasing the current draw. It quickly turns into a self-eating watermelon.
To run a 375-X on 120V power, a 30A circuit (yes, I know it is a 20amp plug) is recommended (15A for 240V). For the purposes of portability (since I can't always count on having access to a 240 circuit), I made a special extension cord adapter that allows me to plug my 375-X and my 150STL into 240V by pulling the hots from two separate 120V circuits at once. Thus, my amperage requirements are only for about 15 amps. Voila! problem solved.
Ammonia refrigeration tech
Trailblazer 302 (yes, it's new)
Millermatic 180 w/Autoset
HF-15 High frequency
XR15 w/Push-Pull Gun
Victor O/A, DeWalt, North mask
"A professional knows what to do. A craftsman knows why."